|发布时间：2019/5/25 14:20:31 浏览次数: 692|
在制冷工况下冷量缺乏 ，有冷风但室内不冷。 房间太大或门窗翻开，请关严门窗。 室内人太多或有热源，请肃清热源。 室外机装置位置不佳，散热不良，如日晒、通风不良等，请校正或重装。 室内机位置不佳，冷气循环差，请校正或重装。 e. 过滤网脏堵，请清洗。 系统梗塞，检查毛细管、过滤器、两器等，请修复或改换。 两器脏，请清洗。 进出风处障碍物，请肃清。|
Under refrigeration conditions, there is a lack of cooling capacity, cold air but not cold indoors. The room is too big or the doors and windows are open. Please close the doors and windows strictly. There are too many people or heat sources in the room. Please clean up the heat sources. Outdoor units are not well positioned and have poor heat dissipation, such as poor sunshine, poor ventilation, etc. Please correct or reinstall them. The position of indoor machine is not good and the air circulation is poor. Please correct or reinstall it. E. Filtration screen is dirty, please clean. System infarction, check capillary, filter, two devices, etc., please repair or change. Clean both organs, please. Obstacles in and out of the wind, please remove them.
制冷剂过多，请放出适量的制冷剂。 系统混有空气，放氟，抽真空，重新灌注。 室外温度太高。 查上下压能否正常，若低压偏高，则系统中可能会有空气，低压偏低，则可能制冷剂走漏、系统缺氟。 若毛细管处结霜，可能是系统中混有水份，形成冰堵，也可能是脏堵。 紧缩机自身效率低。 室外环境温度太高。空调器才能有限，不能冷到所希冀的温馨温度。
If there is too much refrigerant, please release a proper amount of refrigerant. The system is mixed with air, fluoride is discharged, vacuum is pumped and re-perfused. Outdoor temperature is too high. Check whether the upper and lower pressures are normal. If the low pressure is high, there may be air in the system. If the low pressure is low, there may be refrigerant leakage and fluorine deficiency in the system. If the capillary frosts, it may be mixed with water in the system, forming ice blockage, or it may be dirty blockage. Compressor itself is inefficient. Outdoor ambient temperature is too high. Air conditioners are limited and cannot be cooled to the desired warm temperature.
凝器结灰严重，通风不畅，散热效果差，形成空调器制冷量降落。 空调装置位置。室外机组受日晒；室内机组位置太高、太低、偏角，形成冷气循环不良。 制冷循环系统梗塞。毛细管或枯燥过滤器梗塞后，流入蒸发器的液体制冷剂减少，制冷量降落。统高压维
The condenser has serious ash condensation, poor ventilation and poor heat dissipation effect, resulting in a drop in the refrigeration capacity of the air conditioner. Position of air conditioning unit. Outdoor units are exposed to sunlight; indoor units are too high, too low, and deviation angle, resulting in poor air-conditioning circulation. Refrigeration cycle system infarction. After the capillary or dry filter is blocked, the liquid refrigerant flowing into the evaporator decreases and the refrigeration capacity decreases. Unified high-voltage dimension
©2002-2015 上海春普空调设备有限公司 All rights reserved. 备案号：沪ICP09065509号